Honeywell Aquatrol AQ Series electronic controls combine functionality with ease-of-use, making them the perfect choice for nearly every application. Aquatrol is a straightforward, versatile controller which forms the basis of .. The Aquatrol controller can be surface mounted in either a control panel. Honeywell STC Central Heating And Hot Water Timer. EUR ; 1 bid; + EUR postage. 1d 23h left (Sunday, ).
|Published (Last):||21 April 2007|
|PDF File Size:||7.53 Mb|
|ePub File Size:||4.82 Mb|
|Price:||Free* [*Free Regsitration Required]|
User manual HONEYWELL AQ – Download your HONEYWELL AQ user guide or user manual
Lastmanuals offers a socially driven service of sharing, storing and searching manuals related to use of hardware and software: If this document matches the user guide, instructions manual or user manual, feature sets, schematics you are looking for, download it now.
Download the complete noneywell guide Ko. In any way can’t Lastmanuals be held responsible if the document you are looking for is not available, incomplete, in a different language than yours, or if the model or language do not match the description.
Lastmanuals, for instance, does not offer a translation service. Designated trademarks and brands are the property of their respective owners.
HONEYWELL AQUATROL (AQ) – heating control. – £ | PicClick UK
Detailed instructions for use are in the User’s Guide. A wide range of compatible sensors, a remote unit, valves and hlneywell complement the control system.
If there is extra heat available and the boiler temperature is more than 20 K above the DHWS setpoint, the mixing valve will be controlled at the calculated setpoint. The mixed water temperature setpoint is reduced when the boiler temperature lies between these two values.
Cycle Rate Adjustment The cycle rate adjustment allows the cycle rate as recommended by the boiler aquahrol to be set directly on the controller. Heating Curve Ratio Adjustment If a fixed value of the heating curve ratio is required then this value can be set within the range 4 to 40 using this potentiometer. To determine the heating curve required refer to the graph displayed below.
The boiler calculated setpoint will be the mixed flow calculated setpoint plus the set differential. When the controller is in honeywelk mode the boiler low limit will be active from the beginning of the first comfort period to the end of the last comfort period each day.
System Selection System selection is achieved in two manners: Plastic with integral Pg11 fitting: It should be mounted on a bend on the flow water pipe providing a temperature input signal to the controller Ordering Specification: It can be inserted in a well to provide a asuatrol input signal to the controller. Search for a user manual.